Fines, Complaints, and Inspection Problems in the Past 2 Years
Note that this facility has only accepted Medicare for 2 years.
The state and national averages include problems for the past 3 years.
Compare The Number of Problems
Types of Problems at Nursing Homes
Some issues within a nursing home are much more severe than others.
Medicare evaluates each problem based on 2 scales: the number of residents affected by a problem and
the severity of the potential or actual harm to residents based on the problem. We have color coded the matrix below
to make it easier to pick out the more severe problems. In general, orange and red issues related to the treatment of a resident
are considered substandard quality of care.
|Severity of the Deficiency
|Immediate jeopardy to resident health or safety
|Actual harm that is not immediate jeopardy
|No actual harm with potential for more than minimal harm that is not immediate jeopardy
|No actual harm with potential for minimal harm
February 9, 2015 - 2 years ago
| ||Residents Affected||Severity||Source/Type||Description|
|F||Many||Potential for Harm||Fire Safety Inspection||Exit doors that are held open by devices that will automatically close on the activation of a fire alarm or smoke detector.|
|E||Some||Potential for Harm||Fire Safety Inspection||Corridor and hallway doors that block smoke.|
|E||Some||Potential for Harm||Fire Safety Inspection||Smoke barrier doors that can resist smoke for at least 20 minutes.|
|E||Some||Potential for Harm||Fire Safety Inspection||Corridors that are separated from use areas by walls constructed to limit the passage of smoke.|
|C||Many||Potential for Minimal Harm||Fire Safety Inspection||Properly working alarms on sprinkler valves.|
|C||Many||Potential for Minimal Harm||Fire Safety Inspection||An approved installation, maintenance and testing program for fire alarm systems.|
|D||Few||Potential for Harm||Fire Safety Inspection||Portable fire extinguishers.|
|D||Few||Potential for Harm||Fire Safety Inspection||A written emergency evacuation plan.|
|D||Few||Potential for Harm||Fire Safety Inspection||A two-hour-resistant firewall separation.|